This case study pertains to a temperature mapping study and qualification carried out in Riyadh, Saudi Arabia. The process was carried out jointly by Cryopak, USA along with regional partner Vacker Arabia.
Scope of Qualification Process
The scope was to carry out temperature & humidity qualification of a cold room utilised for storage of medicines and vaccines. The cold room needed to maintain a temperature range between 2 and 8 Degree Centigrade and a humidity under 60%.
The cold room was newly constructed and the qualification process was carried out before actual use.
Methodology of Temperature Mapping study
Temperature and Humidity mapping study was carried out for a couple of weeks under various conditions. Since the cold room was new, we could test the same under different conditions.
Methodology of Qualification Process
A protocol was prepared specifically for this cold room. Various tests and verification were carried out as part of the qualification process under the following categories:
- Installation Qualification
- Operation Qualification
- Maintenance Qualification
The temperature mapping study gave good results. However, humidity distribution was not proper and exceeded 75% many times. Other tests of the qualification process were satisfactorily completed. Since humidity distribution was not within the range, the cold room could not be qualified.
Corrective actions for qualification
It was obvious that corrective actions were required for reducing the humidity. Cold room dehumidifiers are required for reducing the humidity.
Dehumidifier for cold room
Dehumidifiers were installed by our operation team to reduce the humidity. The number of dehumidifiers and their capacity was determined based on design calculations. Design calculations are based on the following factors:
- Size of the room
- Required temperature to be maintained
- Required humidity levels
- Present temperature and humidity levels
- Ventilation methods
Two numbers of desiccant type dehumidifiers model TTR 400 were installed at two different corners of the cold room. These are special cold room dehumidifiers, Each was having its own control setting in which we can adjust the desired humidity levels.
Retesting for Temperature and humidity
After installation of the dehumidifiers, temperature and humidity mapping study should be carried out once again.Dehumidifiers are electro-mechanical equipment and will produce a certain amount of temperature. Hence it has to be checked properly and temperature setting needs to be adjusted if required.
In this case, after installation, we did a trial study to check the distribution and adjusted one of the cooling units. After that, a full study was carried out once again.
Results of Mapping study and Qualification
The result of this study was found satisfactory and the cold room was certified after installation of cold room dehumidifiers.
Related articles on Temperature mapping study
- Temperature mapping study and validation
- Guide to Temperature mapping study & Qualification
- Difference between Temperature Mapping Study & Qualification
- Top 10 Checklist for Temperature & Humidity Mapping, Validation & Qualification of cold room, vehicle,warehouse, refrigerator
- Temperature Mapping Study – Pharmaceutical industry
- Temperature Mapping & Qualification of Vehicles, Refrigerator, Cold Room, Warehouse, Reefer
- Temperature mapping study for FMCG industry
Vacker Arabia carries out temperature mapping and qualification in Jeddah, Dammam, Riyadh, Jubail and Khobar in Kingdom of Saudi Arabia.